Raven Lining Systems
13105 E. 61st Street,
Broken Arrow, OK 74012
Lloyd Czerwonka, S&L Industrial Inc.
MUDD District 33
Date of Project:
Type of Structure(s):
Bolted, galvanized steel, 250,000 gallon potable water tank.
Condition of Structure(s):
Condition before restoration included 72 holes in the shell, seam leaks and 124 holes in floor
Description of Application:
Surface preparation of near white blast was performed. Following surface prep,large holes were patched and fiberglass mesh inlaid. Walls were coated with three coats of AquataPoxy® A6 at 5-8 mils; total DFT of 16-24 mils; floor total DFT of 40 mils. An inspection in 1999 revealed the tank to be in “as good as new” condition.