Raven Lining Systems
13105 E. 61st Street,
Broken Arrow, OK 74012
11th and Grove Street, Charleston, South Carolina
City of Charleston
Date of Project:
Type of Structure(s):
Brick manhole 15′ deep, 4′ diameter, with 30″ CIPP rehabbed line and 10″ dead line.
Condition of Structure(s):
Pipe joint leaking and bench severely eroded with voids
Description of Application:
Rehabilitate and coat to low flow but unable to divert or plug lines. Hydraulic cement was used to fill large voids where mortar missing 1/2″ and greater. The bench was rebuilt, voids filled and chemical grouts were injected up to 2′ into the annular spaces surrounding the CIPP line where infiltration was visible. Raven 405 was applied at minimum of 125 mils providing structural enhancement and corrosion protection.